Another day in the life of our service techs. While performing a detailed inspection we identified tube and tube sheet issues. Steve is now inspecting the repairs before the hydro test. After that, this boiler will be ready for the heating season. #boilerrepair#boilerroom#florida#georgia#iecboilers
Gas safety check for market leading property agents @danielbrewer_ea, thoroughly checking all components inside and out ✅
Customer called the gas board out when they had a strong smell of gas from their daughters bedroom at Kelmscote Road Coundon Coventry.
The gas board didn’t find any drop on the gas pipework and the customer was left to keep trying and also worried about even using their boiler.
The customer called me and I attended the property. The first thing they said which had me thinking was that it wasn’t all the time, but had recently been worse with the recent bad and especially windy weather.
I began an inspection on the boiler and found it to a poorly installed boiler. The previous installer had cut the flu to short and just left a huge whole and had attempted to seal it with silicone. This resulted in the the products of combustion ie gas coming back into the room especially on a windy day.
Fortunately nobody was hurt as a result of this as it could have been worse. It was a used bedroom with a family member.
We replaced the boiler flu with new and it was cut to the correct size. We sealed the hole correctly using sand and cement and also serviced the boiler and it will be now looked after every year.
Always make sure any gas work is carried out by a gas safe registered installing and most of all serviced regularly. Be safe not sorry!
If you would like to use my services you can call or drop us a text on 07853554993 or direct message us.
Утро следующего дня вышло более позитивным, чем вчерашний вечер. Мы заменили "голову" с масляным насосом клапана siemens skp25 на новую и заново настроили горение. Теперь расход газа на первой и второй ступени соответствует необходимым показателям мощности.